Two Way Light Switch Wiring
Have you ever wonder how a lamp that is used to light up the stairs of a building is connected to the two switches that controls it from either end? These two way switches have a single pole double throw (SPDT) configuration.
Each has a common terminal (COM) with a pole that can be switched between position L1 or L2. The two way light switch wiring can be implemented by using 2 different methods. Both of the methods used are described below.
The first method as shown in the figure above have the COM, L1 and L2 of both the SPDT switches connected together. For incandescent lamp, the recommended wire gauge used is AWG #14. The LIVE AC Source is connected to L1 of SW1 and one side of the load is connected to L2 of SW2. The other side of the load is then connected to NEUTRAL of the AC Source. With this configuration, the lamp will be turned ON when one switch is at ON position and the other is at OFF position. If both switches are in the same position, the lamp will be OFF.
The other method is as shown in the figure above. In this configuration, the L1 of both SW1 and SW2 are connected together. Similarly, the L2 of both SW1 and SW2 are connected together. The LIVE of the AC Source is connected to COM of SW1 and one side of the load is connected to COM of SW2.
The other side of the load is then connected to the NEUTRAL of the AC Source. With this configuration, the lamp will be turned ON when one switch is ON and the other is also ON. If both switches are in different position, the lamp will be OFF.
Take note that as the installation involves mains power supply, only those who are qualified and have electrical wiring knowledge should do this wiring. When doing the wiring, it is recommended that the power supply is disconnected from the load and the switches.
Back To Light Switch Wiring Home Page
oin electronics design contest and win prizes. Test your hardware and software skills against the best designers from the rest of the world.
Join the electronics events to enhance your knowledge and network with other professionals in this industry.
Some engineering free magazine available for you to subscribe today
Explore the use of 7-Segment Display, 555 Timer, Decade Counter and Binary Adder. Get the circuit.
Design and build a battery tester to test dry cell and rechargeable battery with a voltage of less than 2V. Check here.
Construct this simple door bell chime and have fun. Find out more here.
If you are looking for electronic kits, electronic gadgets or robotic kits, get them here.
Build this simple home alarm to protect your house from intruders. See the schematic circuit.